Project Skills Solutions were engaged having submitted the most competitive quotation to carryout the Fixed wire test and inspection of a Junior school in Essex.
The electrical testing required 119 circuits and 12 distribution boards to be tested in the summer holidays.
The fixed wire testing and certification would involve the following:-
– There will be a visual inspection of the installation
– There will be a Earth fault loop impedance test conducted
– There will be an Earth electrode resistance tests conducted (if applicable)
– Testing of the CPC and earth bonding
– Ring main continuity test (if applicable)
– Insulation Resistance test
– Polarity test
– RCD test
EICR Electrical Testing
Once completed the a full report was issued detailing any failures and there their failure code
Code C1 “Danger Present”. Risk of injury. Immediate remedial action required.
Code C2 “Potentially dangerous”. Urgent remedial action required.
Code C3 “Improvement recommended”.
Code FI “Further investigation required without delay”.
It is surprising that on most fixed wire tests on buildings we find faults even those that have had regular tests. Building particularly schools are extremely busy places and with occupants using areas that may have possible exposure to electrical faults it is essential for these tests to be carried as required by the HSE.
The failures vary from blanking plates missing on distribution boards (please see attached pictures for reference) that are often removed for electrical works but not refitted which results in a C1 failure “Danger Present”. Risk of injury. Immediate remedial action required. These boards are generally in restricted access areas so not a direct hazard to the general public but require immediate rectification simply with a plastic blanking plate being inserted. Another regular failure is electrical works not being done to a good standard or compliant to the latest regulations.
The remedial works are always brought to the attention of the client throughout the testing period and all the required remedial works quoted for withing 24 hours of the EICR being issued.
All codes showing failures were rectified and a new electrical certificate issued on completion allowing us to leave the school in an electrically safe condition for the start of the new term.